|Type Of Current Transformer||Ring Type Tap Wound|
|Dimention||If Special type OD, ID, HT|
|Class Of Accurecy||As Per Costumer Requirement ( 5 or 3 or 1 or 0.5 or 0.2)|
|Make||" KAY PEE "|
|Ratio Of current transformer||As Per Customer Requirement|
|Rated Burden Of CT||As Per Costumer Requirement (2.5 VA To 30 VA )|
Ø Current Transformer
According to IS 2705 this guideline covers application of current transformer for use with both electrical measurng instrument and meter [Measurng current transformer] and electical protective devices in non balanced protected equipment for example for the operation of overcurrent devices both of the non directional and directional type and for the operation of earth fault devices with time lag charateristics [protective current transformer]
It has been made to the use of current transformer for dual purpose of Measurment and protection also for the operation of those protective devices which are more precisely dependent upon the magnitude and phase relationshp of voltage ans current, or upon the balance of current.
This type of transformer are use of frequence from 15 to 100Hz.
Spacfic requrement for current transformr for use with measuring And instrument,integrating meter and smmilar appratus.it also applies to the measuring core of multi core current transformer.
Protective Current transformer For Special Purpose Application Such As Balance Protective Systems And Distance Protection Schemes. It Also Applies To Protective Core Of Multi Cores Of Multi Core Current Transformer Such Application
Ø Type Of Current Transformer
Wound Primary Type Current transformer : A Current transformer Having A Primary Wnding Of More Then One full turn Wound on the Core (s)
Bar Primary Type Current transformer : A Current Transformer In Which The Primary winding Consist of a Bar of Suitable Size and material formng an integral Part of The current Transformer
Dry Type Resin cast Current transformer : A Current Transformer In Which Core And Winding Are Bonded By Resin
Dry Type Current transformer : A Current Transformer which does not Require the use of any liquid Or semi Liquid material.
Liquid Immerced Current transformer : A Current Transformer Which require the Use of Oil or Othr Suitable liquid Of Suitable Charactristics As insulating And/Or Cooling Medium.
Harmetically Sealed Current Transformer : A liquid immerced current transformer Which is Sealed And does not communicate with atmospheric Air
Ring type Current transformer A Current Transformer Which Has An Opening In The Center To Accommodate Primary conductor through it
Multi Core Current transformer : A Current Transformer havingmore Then one Ratio is obatainable By Reconnection, or tappings In Primary or Secondary Winding
Multi Ratio Current transformer : A Current Transformer In Which more Then One Ratio Is Obtainable by Reconnection, or Tapping, in Primary Or Secondry Winding.
|Primary Voltage||35 Kv|
|Secondary Voltage||420 V|